As an independent HVAC contractor, Nationwide Heating & Cooling have the advantage of an excellent choice of manufacturers’ products to work with.
We are able to design schemes for all mechanical building services, from simple Air Conditioning split systems to more complex full building Chiller, Air Handling Units, VRV systems and bespoke stand alone rooms delivering a wide range of air cleanliness, temperature and humidity control.
With projects, we offer the full manufacturers warranty, which can be as much as 7 years subject to regular maintenance being carried out.
NATIONWIDE HEATING & COOLING - celebrating 10 years of providing complete turnkey mechanical services.
What to expect from our design process:
Discuss your requirements
Site Survey to gather information
Installation of your new system
Air Conditioning split systems
Air Handling Units
Our Expertise in:
NATIONWIDE HEATING & COOLING Ltd offer complete turnkey packages for our clients, ensuring that all of our projects run smoothly from inception to completion.
To enquire about our services, please contact us.
PROJECT NAME & LOCATION: GENTOO HAVELOCK BUILDING BOILER PLANT UPGRADE
CLIENT: GENTOO GROUP
PROJECT VALUE: £40,000
SERVICE(S): DESIGN - REPLACEMENT BOILER PLANT
DESCRIPTION OF WORK UNDERTAKEN:
Local Social Housing commercial offices over two floors. Existing boiler plant room housed an Ideal Concord 200kw (4x50kW) modular boiler.
Boiler provided Low pressure hot water (LPHW) for a domestic hot water calorifier and for space heating via radiators and fan convectors. System was vented, with header tanks located in the loft for both the heating and Domestic hot water (DHW) systems. Old system was inefficient and had become unreliable, many spare parts were obsolete and only 2 of the 4 boiler modules were operational.
Old system was replaced with new Ideal Evomax condensing boilers. The client highlighted a preference for a pressurised system which would negate the need for the loft header tanks, but brought other challenges as old pipework and radiators would be operating at significantly higher pressures than before.
At the start of the works, a survey revealed the shell of the DHW Calorifier was leaking and it became necessary to replace this too.
NHC supplied and installed 2 no. Ideal Evo Max 80 Boilers, Ideal 100/150 Concentric Flue System, 300 Ltr Expansion Vessel, Pressurisation Unit and Shunt pump. Works included all boiler connections and pipework and electrical work to boilers and shunt pumps.
New calorifier is unvented and connected directly to the mains water supply and maintained at 2.1 bar via a pressure reducing valve. An expansion vessel allows for thermal expansion of the DHW. BMS TREND system integrated controls for all new plant.